Heat line C24 Pdf User Manuals. View online or download Heat line C24 Installation, Servicing And User Instructions Manual. The boiler’s ‘Log Book’ must be completed at each Service visit. By means of a manual switch the C24/C28 can be set to operate in one of two operating modes, . Boiler Manuals for the Heatline Compact C24 appliance.
|Published (Last):||10 March 2018|
|PDF File Size:||19.36 Mb|
|ePub File Size:||20.61 Mb|
|Price:||Free* [*Free Regsitration Required]|
Fit the new heat exchanger checking that the plate numbers are the same.
Heatline Compact C24
Remove the manifold as shown on the picture below. Naturally domestic hot water demand will draw temporary preference over the heating for the time of how water demand and 3 min cooling period.
Verify that there are no leaks. Disconnect the electrical leads heatline c24 manual air pressure switch connection tube from the fan. The comustion chamber should now be removed, It can be achived heatline c24 manual unscrewing all four side screws.
While doing this lift the panels up 5. Sensor should be heatline c24 manual by using 13 mm spanner 5. Re-assemble the boiler in reverse order. Remove the pump body from the hydraulic assembly by releasing the clip On all installations, after connecting the boiler to the system and initially filling with water, a proprietary inhibitor must be heatline c24 manual to haetline system water to prevent corrosion.
Remove the pressure sensor by turning it in an anticlockwise direction 5. Verify that the appliance DSN code on the screen matches the product code of heatline c24 manual nameplate.
Replace the heat exchanger F77 Fault in gas valve motor Verify the gas valve connections. Re-set if necessary the dip switches heatline c24 manual the potentiometers to values of the old PCB 8. Make sure that all used washers are replaced if necessary. Verify the pump connections.
Troubleshooting Manual |
Verify the boards reference. The sensors electrical heatline c24 manual that dependent on temperature monitors also heatline c24 manual current that is going through the control potentiometers. Verify the pump speed F24 Water circulation fault Verify that the fl ow and return heating isolation valves are open F26 Fault in gas valve motor Verify the gas valve heztline.
Maximum temperature difference reached between return and flow heating. You should unscrew the integral pump vent plug. Verify temperature sensors connections. Make sure that all electrical connections are fit into the right home 7.
Ensure heatline c24 manual gas supply to boiler is turned off 4. Fit replacement sensor 7. Yes Replace overheat thermostats No central heating Is pump running? Pay attention when fitting back the washer 6.
Verify the operation of the gas valve.
Verify the operation of the condensate pump F27 Flame detection fault Verify the flame detection electrode. Primary pressure sensor will turn off your appliance whenever the circuit pressure will fall under 0.
Verify the igniter unit F28 Ignition fault Verify the return gas circuit gas valve open. Open the isolating valves on the flow and return connections. If seals are damaged- replace as necessary 8. Re-set heatline c24 manual Whenever boiler gets locked out, you should verify the gas supply and ionisation probe position.
Open a hot tap to create a demand — is there heatline c24 manual spark at the ignition electrode? Remove the front panels by swinging them. The preference is that condensate material should be discharged into the household internal drainage system.
Remove the sensing tube and electrical connections from the air pressure switch, noting which tube is connected to which port as shown heatline c24 manual the heatline c24 manual below. Boiler parts Each Heatline boiler is equipped with following additional parts: